Call anyone of our sales personal and we would be glad to set you up with one of your distributors. If you are a distributor and would like to sell our products feel free to call our sales department to fill out an application.
There is NO ORDER Minimum! You can order as much as you need and only what you need!
Check to see if the 1" o-rings in the swivel connections are cut or torn. Make sure no pipe dope/tape is used on swivels. These should only be hand tight.
Yes, up to 30 feet above the Flow Center.
You must use a Flushcart only if you put your header outside.
Yes. It should only be snugged down hand tight.
Yes. It should be filled at the bottom of the elbow on GT®'s and the top of the elbow on QT®'s.
Yes. The Flow Center is designed with the foot of head needed to work with any heat pump.
No. As long as you are using the GT® or QT® (any non-pressurized Flow Center).
Pumps should be throttled at heat pump, but if no valves are available, throttle with the top ball valve of the Flow Center never the bottom.
We highly recommend a Flowmeter tool but, you may use a pressure drop across the heat pump.
No. It has been tested by the manufacturer of the pumps that it will not cause cavitation.
The water shouldn’t rise more than 3/4”. If it rises more that that it has air in the system and must be reflushed.
No, because it will pump through the other flow center which will push the lid out.
No, because there is too much pressure and it will blow out bottom or top of Flow Center.